Description: This users manual for Altistart 46 soft start motor controllers contains installation, setup, operation, and maintenance instructions. User’s manual ATS46, 9/21/18, English, Spanish, French, pdf MB. Data Bulletin. Cross Reference Guide for ALTISTART® 46 Soft Start Motor. User’s manual UNI-TELWAY ATS VW3G, 12/13/17, English, pdf MB. Programming manual ATS VW3G, 12/13/17, English.
|Published (Last):||21 October 2008|
|PDF File Size:||11.45 Mb|
|ePub File Size:||10.67 Mb|
|Price:||Free* [*Free Regsitration Required]|
Expanded polystyrene is not allowed. Care should be taken to ensure that this card is positioned correctly, placing the connectors towards the top of the unit. The motor starts without following the normal acceleration.
Insert all the wires through the centre of the bracket. J 49 Follow the diagram: Measurement card Screws Brackets 7 – Remove the fan cover two screws with a 7 mm manuual. Location of screws for connecting the rating card Screw 8 – Reconnect the rating card of the kit.
Altistart 46 – Downloads | Schneider Electric
The motor starts if a 2-wire control is on Maunal value equal to 0 during powering up, even though its value is different refused of to reset to zero the parameter TFR hourmeter when the engine is running on-factory adjustment of parameters IPR, TPR and TBS local mode used only upon the first product powering up assignment of LI to LII motor preheating or LIH faults inhibition default startup time when loaded went to 4 seconds removal of the starter thermal protection calculated by the software on C11, C17, C21, C25 and C32 calibre readjustment of the rated current value by on-factory setting A for M12 calibre correction of altistzrt anomaly concerning the micro controller upon unshunting with the bypass function correction of the anomaly following a simultaneous running instruction with a stopping instruction.
Minimum resistance has to be 50 kilo-ohms. This briefing has altidtart be transmitted to the customer and to DAS altistarrt must contain the following information: Knowledge required – Knowledge of the main applications cooling, pumping, horizontal handling. Active during normal operation.
During a start-order on contactor with software version inferior to V1. FrF or 50 or 60 Hz. External fault order Operating state Up to now experience: SY3CM Green wire mark 2: For onsite work, a communication interface must be available for adjustment, when required. V 1 Rated ef f. Run the cable to the penultimate right-hand plug-in unit for a size 4 starter or 466 the centre of the starter for a size 5.
Altistart-« 46 Soft Start Motor Controllers Users Manual
SY3CM Blue wire mark 3: Remove the connectors located at the base of the product. The pump transformer must be removed.
Phases off-balance due to insulation defect on IT rate 1. Fan 2 3 0V 1 8 5W Recommended torque load for screw M4: Remove the transformer by unscrewing the CHC screws using a altistarf mm Allen key.
Strip the wire and insert it in the clips.
Version Date of selling V1. Conversion instructions for size 3 9 – Install the connectors in the locations behind the control module of the Altistart according to the markings. Their value is calculated to obtain rated current of each coiling for primar y rated voltage. Reassembling as an Altistart 46 1 – Reattach the transformer using the four fixing screws, with the cabling on the left-hand side of the unit. Outlet order mxnual not important. Core housing Material U.
User’s manual ATS46 | Schneider Electric
Starter disrupted by a DC converter 1. The product structure is identical to the one of ATS23, that is to say, a control element common to all sizes, and a power element specially designed to each calibre.
VW4G Moreover, all spare parts are also delivered with instruction bulletins. Please refer to page 7 for the wiring of the customer terminal block. Assembly size 5 Parts list Part 6: This conversion can only be performed on products dated later than the following weeks: At each design and manufacturing step, the products are processed with great care. OLF acknoledgement, followed by a start request are done as following: To install this software: For units with two transformers only the right-hand transformer viewing the unit from the front is to be removed.
Starting end on a high inertia, low opposing torque application. The quality of the replacement service is based on stocks constituted at Evreux, in the branches and by the official dealers. Humidity test according to IEC and 3.
Fan Screw Transformer Conversion a,tistart for size 3 Remove the thyristor cables. If the conditions are dif ferent, they have to be specified in chapter 7: Attach the assembly with plastic clamps in the appropriate locations.
Screws Fan view from above 9 – Disconnect the two power supply wires from the transformer from the fan manjal wire with white cable end.
J 43 Conversion instructions for sizes 4 and 5 6 – Wiring the control cables of thyristors J4 to J9. If, for practical reasons, you do not want to disconnect the protection and control circuits, top to bottom terminal resistance can be measured. USF power supply fault, when start mode is required Up to now experience: altistary